What's the Difference Between Class A and Class B?
-- The Fire Alarm System is a Life Safety System - so the occupants of a building can escape quickly, the idea behind a Fire Alarm System is that it will provide a warning that there is a fire. The trouble is, if something is wrong with the system, like a wire is broken somewhere in the building, the Fire Alarm System... Read More
What Causes an Open NAC?
-- I am going to a job site where on the service call ticket states that a NAC is reading open circuit. What can cause an open circuit on the NAC line? Read More
How Does the Panel Know the Address?
-- When a fire alarm system is first set up, there are two types of devices that are programmed - one type of device is the Control Panel and the other type of device are all the smoked detectors, heat detectors, pull stations, flow switches, relay outputs, etc...Read More
Do I Have to Use a PVC Pipe That's Listed?
-- The word Listed means that a nationally known, third-party testing laboratory like UL, ULC, CE, FM, etc. has tested the pipe for use in Aspiration Systems for Air Sampling. Once the testing laboratory knows that the pipe is going to be adequate for this purpose, they say that it is adequate by...Read More
Are Speaker Circuits Required to be Classified?
-- Classification isn't really the exact method of installing wires, classification is knowing how the system deals with failures. When something goes wrong with the system, does the fire alarm system warn the building owner that there's a problem? Is there a method to get around the problem so the system will detect-and-warn even if there's a problem?...Read More
Why is There an EOL Resistor on a Pressure Switch?
-- In a fire alarm system, all devices have to be continually checked to make sure they never come loose. For conventional devices on Class B systems, like the pressure switch, the best the fire alarm panel can do is make sure the wires are always connected. The resistor is used to make sure...Read More
What is a Repeater Panel in a Fire Alarm System?
-- A Repeater panel is used in a remote location, away from the control panel. It passively displays the condition of the fire alarm panel. If there are control buttons on the Repeater panel, it can also actively control the fire alarm system. A LCD display is an expanded version of the Repeater panel...Read More
What is a Fire Alarm System?
-- The idea behind fire alarm systems is to save lives and protect property. A fire alarm system does this by detecting fire -either automatically or when someone sees a fire- and then warning everyone in the building about the fire. A person, having seen a fire, could run down the halls shouting...Read More
Where Should I Install the Fire Control Panel?
-- If all the horns and strobes in the entire building sound off so everyone in the building leaves in less than five minutes, then any fire protection of the fire alarm system only has to be good enough for everyone to leave. If only some of the people are told to leave, and some people wait their turn to leave, then once a fire starts, any fire alarm equipment including...Read More
How are Lamps Tested on Fire Alarm Panels?
-- The purpose of the lamp test is to catch problems with the lamps before there is a fire. In the olden days, before there were LED lamps, there were incandescent lamps. Incandescent lamps used a small wire -the filament- that got hot enough to produce light. It may take many years, but eventually all incandescent lamps burn out; their filaments burn out. Some will burn out sooner than others...Read More
Should the HVAC System be Shut Down on Alarm?
-- The idea behind the fire alarm system shutting down the HAVC in case of fire is that the fire alarm shutting-down the fans will save lives. When a fire is detected, rather than allowing the whole building to fill smoke, the fire alarm system closes the fire doors, closes the fire dampers in the ductwork, and shuts down the air circulating fans...Read More
How Important is it to Label Wires?
-- Good options for the labels come in two varieties --- Labeling Machines - The labels look good, but care must be taken in choosing the machine type. --- Cloth Tape - The labels looks ugly, and care must be taken in choosing the tape type. However, the writing put on the tape using sharpie pens NEVER rubs off... Read More
What do Alarm Output Modules do on the SLC?
-- The Signaling Line Circuit -SLC- for the building wiring for a fire alarm system is the communication and power circuit that is connected between the fire alarm panel and the Addressable Input Modules -AIM- and devices, and the Addressable Output Modules -AOM-...Read More
What is the Trigger Voltage for a Booster Power Supply?
-- Most fire alarm control panels can provide a limited amount of power for the horns and strobes, but extra power for the horns and strobes can be provided by a Booster Power Supply -BPS-. The term -Trigger Voltage- for the BPS is a shorthand term for -Whatever voltage is necessary to turn on the Booster Power Supply-. Depending on...Read More
Are Breaker Locks Required if There's No Control Panel?
-- A Fire Detection and Alarm System is a system that detects fire and warns people of danger. As such, it should never be turned off; it's a life-safety system. If it's 120-volt detectors and pull stations connected to relays that sound bells throughout a building, it's still a life-safety fire alarm system. If it ever was turned off, people occupying a building would not be warned of a fire...Read More
How do I Address the Pull Stations?
-- The numbers that you dial into the devices are address numbers. They're shortcut addresses. Instead of saying -Pull Station, 2nd Floor, North Stair- you dial in the 2 digit number. It's much easier for the electronics to use a 2 digit number instead of the long description; the short number takes a lot less time to send than the long description...Read More
How are the Horns and Strobes Activated?
-- A fire alarm system is a Detect Fire and Warm People about the Fire system. It has automatic detection devices like smoke detectors, heat detectors, and waterflow switches -- it has manually operated input devices like pull stations and MCPs -Manual Call Points-. The detection devices send their alarms to a Fire Alarm Control Panel or FACP. Automatically deciding what to do when there are alarms, the control the control panel has circuitry to sound the alarm. Providing electrical power to...Read More
Are Addressable Fire Alarm Systems Different from Conventional Systems?
-- Many fire alarm people think that an addressable fire alarm system is totally different from a conventional fire alarm system. But is it? A NAC circuit -Notification Appliance Circuit-, for instance, is a totally conventional circuit. Any addressable panel that has a NAC circuit has a conventional NAC circuit. If there are..Read More
What is Voltage Free Interfacing?
-- The terms -Potential Free- or -Voltage Free- are engineering terms for -The module has relay contact outputs only-, and it doesn't provide power for anything, or supervise anything -- it doesn't check continuity of any wires. It also doesn't provide power or voltage to activate anything...Read More
What Happens to the SLC when a Device is Disconnected?
-- A Signaling Line Circuit (SLC) has two purposes: (1. An SLC is used to send signals between the control panel and the devices on the loop (2. An SLC is used to provide power from the control panel to the devices on the loop. To understand what is going on electrically...Read More
What do We Include in Battery Calculations?
-- When deciding what to include in the battery calculations, we look at the reasons for making these calculations in the first place. A fire alarm system is a life safety system; if the system doesn't work, people can get hurt - or worse. The times that the fire alarm system is supposed to work are -Always-, including the time during a power outage...Read More
What is the Difference Between Class A and Class B NAC Circuits?
-- The short explanation is that coming into the panel for Class A, there are a total of 4 wires, and for Class B, there are a total of 2 wires. However, to understand that short explanation, one needs to know the difference between Class B and Class A from a life-safety point of view. Electricity has to get to the horns and strobes in order for the horns and strobes to warn people of a fire. For electricity to flow, however, the electrons require a complete electrical path. Electrons cannot flow through a wire, unless there is somewhere to go...Read More
Can the Fire Alarm Zones be for Multiple Floors?
-- A zone on a fire alarm panel display is shown either with labeled lights -like "Basement", "1st Floor", "2nd Floor", "3rd Floor", Etc.- or with words on a graphic display. -- A zone is where you are going to send the fire department when there's a fire -- A zone is where you are going to send the building owners when there's a false alarm -- A zone is where you are going to send the fire alarm technician when the system needs fixing -- If the fire alarm system is an addressable system that uses words on the display, all the devices are shown as separate devices, each device is actually ...Read More
What is the Maximum Number of Zones Permitted?
-- The NFPA (National Fire Protection Association) doesn't decide how many inputs or outputs can be on a fire alarm panel, and they don't decide how many zones we can attach to a fire alarm control panel. These decisions are left up to the manufacturer of the panel. The NFPA, however, does indirectly control how well the panel is going to work. Once the panel is designed and ready, the manufacturer has to get the panel tested by a...Read More
How is the Standby Power Calculated?
-- In case there's a power outage, the fire alarm system still has to detect fire and warn people of fire. It would be nice if the fire alarm system could do this for days, weeks, or even years, until eventually the power can be restored, but the NFPA (National Fire Protection Association) is reasonable. In most cases, the NFPA is happy if the system can continue to work without power for 24 hours. This is the standby period. If there is a fire detected at the end of that 24 hours, the system still has to sound the alarm. Usually sounding the alarm takes up a much higher level of current than when the alarm system is standing by, so sounding the alarm has to be calculated separately. This is...Read More
What Is the Difference Between Conventional and Addressable?
-- The word conventional doesn't mean Old and Obsolete, the word conventional means Sanctioned by General Custom. The conventional fire alarm system is the standard way, or ordinary way of making a fire alarm system. The Addressable portion of a fire alarm system isn't a replacement for a conventional fire alarm system, the Addressable portion is ...Read More
How is a Pathway Classified?
-- The classification for a pathway is not determined by the method of carrying a signal or the type of signal the pathway is carrying - The classification is determined by what the pathway isn't or can't do - the classification is a process of elimination...Read More
What is Class N Power Over Internet (PoE)?
-- Powering detectors and modules, Class N communication paths using Power over Ethernet (PoE) is coming to a fire alarm system near you. Probably not all of the systems or devices will use Class N PoE paths, but enough...Read More
Is an EOL Resistor Needed for an Addressable System?
-- Normally, as I know, an addressable fire alarm circuit is without end of line resistor and conventional fire alarm circuit has an end of line resistor... But I found some documents online showing the FAS (Fire Alarm System) to work using an end of line resistor to measure electrical current and resistor. So how does an addressable system work? Read More
What is a Four Wire Smoke Detector?
-- A 4-wire smoke detector is just like a 2-wire smoke detector, except that it receives its power from an auxiliary power supply rather than the conventional Initiating Device Circuit. Both the 4-wire and the 2-wire smoke detector sense particles in the air and call the particles smoke... Read More
NFPA's 7 Classes of Fire Alarm Paths
-- The NFPA has divided the signal paths in a fire alarm system into 7 classifications: Class A, Class B, Class C, Class D, Class E, Class N, Class X. These classifications don't show how to wire up anything, these classifications show what happens when things go wrong... Read More
Why Doesn't a Smoke Detector Always Detect?
-- The NFPA wants smoke detectors tested in place to make sure smoke enters the smoke chamber. Keep in mind that a smoke detector can't detect smoke that doesn't get to the detector. When a smoke detector doesn't... Read More
Firefighter Don't Reset the False Alarm
-- When the alarm sounds and the firefighter arrives, even for a false alarm, the firefighter is on site for property protection and life safety. So when leaving, from the point of view of the firefighter, the ... Read More
What is a Fire Alarm Zone?
-- Building zones aren't determined by where the wires are run for the fire alarm system, building zones are determined by the building's fire-control -- fire-fighting divisions and by the building's smoke-control divisions... Read More
What Is Fire Alarm Trouble Power?
-- In the "Old School" type of fire alarm system, before the smoke detector was invented, even though the fire alarm systems used AC, all voltages were in a steady state: either on or off. Until someone ... Read More
If It's There -- It Has To Work
-- Whether its smoke detectors on the ceiling or the firefighter's telephone system, people think that if it's there, it's real and it works. Sometimes, people even stake their lives on that device or system ... Read More
What is a 4 Wire Smoke Detector?
-- Even though it uses an internal protection resistor and internal alarm relay contacts, a 4 wire smoke detector is basically a 2 wire smoke detector; it detects smoke and sends an alarm ... Read More
What Makes a False Alarm so Dangerous?
-- Each false fire alarm increases the severity of a real fire. The increased severity from false alarms comes from the greater chance of loss of life or a greater chance of injury. This is a progression - with no false... Read More
What is an Area of Refuge?
-- You hear the message "Use the Stairs, "you see the sign "In case of fire, don't take the elevator." To get out of the building from the higher floors, when the building is on fire, the stairs ... Read More
Share This With Friends: