# Fire Alarm -- Description

The Initiating Device Circuit uses Voltage produced by the fire alarm panel to drive Current through the wires of the circuit.

The end of line resistor has resistance to allow normal current through the circuit while keeping the voltage at a normal level, showing a normal circuit to the panel.

If the total resistance of the circuit goes up because a wire breaks or a connection comes loose, the current stops, the voltage goes up, and the panel sees trouble.

If the total resistance of the circuit goes down because a device on the circuit lowers its resistance, the current increases, the voltage goes down, and the panel sees an alarm.

# How Does Resistance Affect the Initiating Device Circuit (IDC)?

By Douglas Krantz

IDC circuits (Initiating Device Circuits) are input circuits to the fire alarm control panel, and the wiring is either a Class A or a Class B configuration.

Devices connected to the IDC cause the panel to do something: sound the alarms, operate relays, and call the monitoring company, among other things.

The IDC circuits look for alarm and supervisory signals from pull stations, smoke and heat detectors, waterflow switches, tamper switches, etc. These are all input (initiating) devices.

## Two Wire DC Circuit

IDC circuits are two wire circuits, and are supervised for normal condition, alarm condition, and trouble condition. The voltages, currents, and resistances on the IDC are steady - - no AC or variations in DC levels, except when the circuit changes from normal to alarm or trouble.

## Two-Way Supervision of the IDC

The supervision voltage is produced by the panel on its IDC screw terminals at all times; this voltage pushes the electrical current through the circuit.

In return, the IDC, changing its resistance to affect the amount of current flow, changes the voltage seen by the panel on the screw terminals.

## Three Resistance Conditions of the IDC - - Read by the Panel

The supervision voltage, seen by the panel using an internal voltmeter, tells the panel the circuit is Normal, the circuit has an Alarm or Supervisory, or the circuit is in Trouble.

### Normal - - End-of-Line Resistor Resistance

To confirm that there are no breaks in the wire or the connections, the wires are supervised. Under normal conditions, the current through the IDC is restricted by the End-of-Line Resistor.

The resistance of the wires themselves is too small to be of any consequence. However, for the end-of-line resistor to be detected by the panel, the supervisory current has to pass through all the wires. To confirm that the devices are connected, this supervision current also has to pass through the input terminals of the devices.

By wiring the devices in a Class A or Class B configuration, the panel may not be able to tell if a particular device is working. At least, however, if the device becomes disconnected, the supervision current stops and the panel then shows a trouble condition to the owner.

### Alarm - - Shorted or Partially Shorted Wires - - Low Resistance

This is a condition where one of the initiating devices (detectors, switches, etc.) is shorting out the Initiating Device Circuit, or partially shorting it.

The short causes the supervisory current on the circuit to rise. The rise in supervisory current causes the voltage at the IDC terminals of the panel to drop. The panel interprets this drop in supervision voltage as an alarm or a supervisory signal.

Of course, any other wire-to-wire short on the IDC will also be interpreted as an alarm, even if it's only water on the wires.

### Trouble - - Open Wires or Bad Connection - - High Resistance

If the wire breaks or a connection comes loose, the supervision current drops. The drop in current causes the supervision voltage at the IDC terminals of the panel to increase.

The panel interprets this increase in voltage as a trouble condition.

## T-Taps on the IDC Aren't Acceptable

Yes, if there's an alarm on a device on a T-tap, the panel will see this as an alarm and do what it's programmed to do.
Yes   No

However, when there's a T-tap, the supervision Current doesn't pass through the wires or the ins and outs of devices on the T-tap. If a wire breaks on the T-tap, or a connection to one of the T-tapped devices comes loose, there's no change in the supervisory current so the panel doesn't detect a trouble condition.

No one finds out about the trouble condition until there's a fire, at which time it's too late to start troubleshooting.

To be properly supervised, the devices have to be daisy-chained in a Class A or Class B configuration, and there can be no T-taps.

Note: IDC (Initiating Device Circuit) power, used by the detectors, will be addressed in a later issue of Short Circuit.

Douglas Krantz

Describing How It Works
Text
612/986-4210

The
Technician

Short Circuit
Free Subscription
I'll Send You the
Twice-Monthly
Fire Alarm

Articles

How Does Class A Fire Alarm Wiring Work?-- Fire alarm systems save lives and protect property. Fire alarm systems also break down because... Read More

Just What Is a Signaling Line Circuit (SLC)? -- The SLC (Signaling Line Circuit) is another way of saying Data and Power Circuit. Along with added power to run the sub-computers and their input and output circuits, it's a computer data-buss ... Read More

How is a Buffer Relay Wired Into a Door Holder Circuit? -- Like a door stop, a door holder keeps a fire door open. When smoke is detected, the door holder releases, allowing the door to shut. The door holder looks simple and innocuous enough... Read More

How Does One Find a Soft Ground Fault? -- Normally, we think of resistance like that of a resistor. The amount of resistance is built-in; no matter what voltage is used to drive the electrical... Read More

Can a Magnet Really be Used to Test a Smoke Detector? -- Smoke detectors usually have two ways of being tested. Smoke (smoke particles in the air, or some sort of canned smoke), and magnets (the activation of an internal magnetic... Read More

Electrical Flow

On this website, most references to electrical flow are to the movement of electrons.

Here, electron movement is generally used because it is the electrons that are actually moving. To explain the effects of magnetic forces, the movement of electrons is best.

Conventional current flow, positive charges that appear to be moving in the circuit, will be specified when it is used. The positive electrical forces are not actually moving -- as the electrons are coming and going on an atom, the electrical forces are just loosing or gaining strength. The forces appear to be moving from one atom to the next, but the percieved movement is actually just a result of electron movement. This perceived movement is traveling at a consistent speed, usually around two-thirds the speed of light. To explain the effects of electrostatic forces, the movement of positive charges (conventional current) is best.

See the explanation on which way electricity flows at www.douglaskrantz.com/
ElecElectricalFlow.html
.